Acti 9 iID - RCCB - 4P - 40A - 30mA - type AShow more characteristics >
Main rangeActi 9 product nameActi 9 iID product or component typeResidual current circuit breaker (RCCB) device short nameIID poles description4P neutral positionLeft [In] rated current40 A network typeAC earth-leakage sensitivity30 mA earth-leakage protection time delayInstantaneous earth-leakage protection classType A Complementary device location in systemOutgoer network frequency50/60 Hz [Ue] rated operational voltage380...415 V AC 50/60 Hz residual current tripping technologyVoltage independent rated breaking and making capacityIm 1500 AIdm 1500 A rated conditional short-circuit current10 kA [Ui] rated insulation voltage500 V AC 50/60 Hz [Uimp] rated impulse withstand voltage6 kV contact position indicatorYes control typeToggle mounting modeClip-on mounting supportDIN rail 9 mm pitches8 height91 mm width72 mm depth73.5 mm product weight0.37 kg colourWhite mechanical durability20000 cycles electrical durability15000 cycles AC-1 locking options descriptionPadlocking device connections - terminalsSingle terminal, top or bottom flexible with ferrule wire(s) 1...25 mm² maxSingle terminal, top or bottom rigid wire(s) 1...35 mm² maxSingle terminal, top or bottom flexible wire(s) 1...25 mm² max wire stripping length14 mm (top or bottom) tightening torque3.5 N.m (top or bottom) Environment standardsEN/IEC 61008-1 IP degree of protectionIP40 for modular enclosure conforming to IEC 60529IP20 conforming to IEC 60529 pollution degree3 electromagnetic compatibility8/20 µs impulse withstand, 250 A conforming to EN/IEC 61008-1 ambient air temperature for operation-25...60 °C ambient air temperature for storage-40...85 °C Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profile Product end of life instructionsNeed no specific recycling operations Contractual warranty Warranty period18 months 18 months
Documents & DownloadsLanguage
CADSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.