Main range of productModicon Quantum automation platform product or component typeLow voltage dc discrete input modules discrete input number32 Complementary group of channels4 logic inputPositive (sink) discrete input voltage24 V DC input voltage limits19.2...30 V voltage state 1 guaranteed15...30 V DC voltage state 0 guaranteed-3...5 V DC current state 1 guaranteed>= 2 mA at Us = 5.5 V and Uin = 0 V current state 0 guaranteed<= 0.5 mA addressing requirement2 input words input impedance2500 Ohm leakage current200 mA at Us = 5.5 V and Uin = 4 V absolute maximum input30 V continuous56 V during 1.3 ms decaying pulse response time<= 1 ms from state 0 to state 1<= 1 ms from state 1 to state 0 protection typeInput protection by resistor limited power dissipation1.7 W + (0.36 x number of points on) isolation between group and bus1780 Vrms for 1 minute isolation between group500 Vrms for 1 minute local signalling1 LED green bus communication is present (Active)1 LED red external fault detected (F)32 LEDs green input status markingCE bus current requirement330 mA module formatStandard product weight0.3 kg Environment protective treatmentConformal coating Humiseal 1A33 standardsCSA C22.2 No 142UL 508 product certificationsABSBVC-TickDNVGOSTRINARMRS resistance to electrostatic discharge4 kV contact conforming to IEC 801-28 kV on air conforming to IEC 801-2 resistance to electromagnetic fields10 V/m 80...2000 MHz conforming to IEC 801-3 ambient air temperature for operation0...60 °C ambient air temperature for storage-40...85 °C relative humidity95 % without condensation operating altitude<= 5000 m Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profile Product end of life instructionsAvailable Contractual warranty Warranty period18 months
Documents & DownloadsLanguage
User guideSizeAdd to My DocumentsCatalogueSizeAdd to My DocumentsCertificateSizeAdd to My DocumentsATEX-IECEx (Version 1.0)Declaration of conformitySizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.