Main range of productModicon Quantum automation platform product or component typeVAC discrete input modules software nameConceptUnity ProProWORX 32 discrete input number32 Complementary group of channels4 addressing requirement2 input words discrete input voltage115 V AC input current<= 11.1 mA 57...63 Hz<= 13.2 mA 47...53 Hz voltage state 1 guaranteed79...132 V AC at 57...63 Hz85...132 V AC at 47...53 Hz voltage state 0 guaranteed0...20 V AC at 57...63 Hz0...20 V AC at 47...53 Hz input impedance12000 Ohm capacitive at 57...63 Hz14400 Ohm capacitive at 47...53 Hz network frequency limits47...63 Hz leakage current<= 2.1 mA absolute maximum input132 V continuous156 V 10 s200 V 1 cycle response time4.9...0.75 ms x line cycle Off-On7.3...12.3 ms On-Off isolation between group1780 Vrms for 1 minute isolation between group and bus1780 Vrms for 1 minute bus current requirement250 mA power dissipation in W<= 10.9 W local signalling1 LED green bus communication is present (Active)1 LED red external fault detected (F)32 LEDs green input status markingCE module formatStandard product weight0.33 kg Environment standardsCSA C22.2 No 142UL 508 product certificationsFM Class 1 Division 2CUL resistance to electrostatic discharge4 kV contact conforming to IEC 801-28 kV on air conforming to IEC 801-2 resistance to electromagnetic fields10 V/m 80...2000 MHz conforming to IEC 801-3 ambient air temperature for operation0...60 °C ambient air temperature for storage-40...85 °C relative humidity95 % without condensation operating altitude<= 5000 m Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profile Product end of life instructionsAvailable Contractual warranty Warranty period18 months
Documents & DownloadsLanguage
User guideSizeAdd to My DocumentsCatalogueSizeAdd to My DocumentsCertificateSizeAdd to My DocumentsDeclaration of conformitySizeAdd to My DocumentsEnd of Life InformationSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.