Main range of productModicon Quantum product or component typeEthernet RIO drop adaptor number of port3 integrated connection typeEthernet IP/Modbus TCP (service port)Ethernet IP/Modbus TCP (device network) communication port protocolEthernet IP/Modbus TCP product destinationModicon Quantum device applicationTo provide the ability for a M580 system to control Modicon S908 coaxial bus communication serviceThe input data are collected and published to the remote I/O head adaptorOutput modules are updated with the data received from remote I/O head adaptor Complementary topologyDaisy chain loopS908 bus local signalling1 LED green for RUN1 LED green/red for module status (Mod Status)1 LED green/red for network communication status (Net Status)1 LED red for I/O product compatibilityBMEP584040BMEP585040BMEP586040BMEH584040BMEH586040 environmental characteristicHazardous location class I division 2 conforming to EN/IEC 61131-1Standard environment width167 mm height50 mm product weight0.554 kg Environment product certificationsCEC-TickUL 508 standardsCSA C22.2 No 142EN 55011IEC 61000-4-16 IP degree of protectionIP20 conforming to EN 61131-2IP20 conforming to IEC 60527 overvoltage categoryClass I conforming to EN 61131-2 ambient air temperature for operation0...60 °C conforming to IEC 60068-2-10...60 °C conforming to IEC 60068-2-2 ambient air temperature for storage-40...85 °C conforming to IEC 60068-2-1-40...85 °C conforming to IEC 60068-2-2 vibration resistance3.5 mm constant amplitude (f=0.5...8.4 Hz) conforming to EN 61131-21 gn constant acceleration (f=8.4...150 Hz) conforming to EN 61131-2 operating altitude2000 m altitude transport3000 m relative humidity93 % conforming to IEC 60068 Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profileAvailable Product end of life instructionsAvailable
Documents & DownloadsLanguage
Declaration of conformitySizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.