Bring all of your project information together, and then export the data as a PDF or spreadsheet.Watch the video
Search through articles relevant to your industry.Read now
Schneider Electric Australia Website×
Can ATV312 drive be programmed to have a 3-contactor bypass?
ALTIVAR 312, ATV312
ATV312 is not available as an enclosed product and there are no programming options for a 3-contactor bypass control. However, the drive relay can be configured for drive running that can pull in a DOC drive output contactor (aux contact) to satisfy a run permissive (assigned to a logic input). The bypass and Isolation contactor are controlled through an external control circuit.
Mostly controlled by the control circuit not the drive. In the EFLEX design w/ bypass, the ATV312 drive would connect the same way as an ATV61. LI2 is assigned to run permissive (nSt) which is satisfied the the DOC contactor.
Get the latest on new products, best practices and innovation from Schneider Electric.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!