Bring all of your project information together, and then export the data as a PDF or spreadsheet.Watch the video
Search through articles relevant to your industry.Read now
Schneider Electric Australia Website×
The standard utilization categories defines the current making and breaking values for contactors.
They depend on the following:
This applies to all AC devices (loads) with a power factor of at least 0.95 (cos phi greater than or equal to 0.95).
Example of use: resistive load, heating, distribution.
This applies to squirrel cage motors where breaking occurs while the motor is running.
Example of use: all squirrel cage motors, lifts, escalators, conveyors, bucket elevators, compressors, pumps, mixers, air conditioning units, etc.
The most common application of contactors is controlling squirrel cage asynchronous motors.
Hence, Schneider Electric contactor part numbers are based on the AC-3 rating.
For example, the LC1D18xx contactor is designed to control motors with a nominal current rating of 18 A (AC-3).
This contactor is capable of withstanding current peaks (~ 100 A) on starting, such as are typical on inductive machines like motors, without sustaining any damage.
It can also control resistance heaters for current ratings up to 32 A (AC-1). This load is resistive, hence there are no current peaks.
Get the latest on new products, best practices and innovation from Schneider Electric.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!