Bring all of your project information together, and then export the data as a PDF or spreadsheet.Watch the video
Search through articles relevant to your industry.Read now
Schneider Electric Australia Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Difference between ferrous product to be detected and non-ferrous product to be detected
Ferrous products: any steel
There are sensors which can detect:
Ferrous metals as a preference (steel, iron)
The sensing distances for these products vary according to the metals to be detected: maximum for ferrous metals and dependent on a Km coefficient typical of each metal (value between 0 and 1: Km = 1 for steel)
This coefficient reduces the sensor detection range. For example while Km = 1 for cast iron, it is only 0.25 for copper.
This is the conventional inductive sensor
For both ferrous (steel, iron) and non-ferrous (brass, aluminum, copper, etc.) metals
The sensing distance for these sensors is the same for both ferrous and non-ferrous materials. The Km coefficient is always 1
They are called Ferrous/Non-Ferrous sensors.
The Schneider part numbers are: XS1M18KPM40x, XS1M30KPM40x 18 and 30 diameter sensors respectively and XS7C40KPM40
Selective, either ferrous materials or non-ferrous materials
The Schneider part numbers are: XS1M18PAS40x insensitive to ferrous materials, XS1M18PAS20x insensitive to non-ferrous materials
They are called selective Ferrous/Non-Ferrous sensors.
Difference in detection principles
For both sensors, an LC oscillator creates an electromagnetic signal.
The difference in detection principles for the two types of sensor lies in:
Attenuation of the oscillation amplitude for ferrous materials, it is significant for ferrous materials and insignificant for non-ferrous materials
Variation in oscillation frequency for selective or non-selective ferrous/non-ferrous materials. For high-frequency operation (in the region of one MHz), both types of material (ferrous and non-ferrous) have the same effect on the oscillation frequency variation.
Km coefficient depending on the different metals for inductive sensors
Get the latest on new products, best practices and innovation from Schneider Electric.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!