Bring all of your project information together, and then export the data as a PDF or spreadsheet.Watch the video
Search through articles relevant to your industry.Read now
Schneider Electric Australia Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Auxiliary Contact installation is possible in Two Poles MCCBs same as in Three Pole and Four Pole MCCBs, but it is not possible to install and use OF/SD Auxiliary Contact 29450 in the Single Pole Compact NS MCCB.
Note that you can only have the either OF or SD information with this 29450 Auxiliary Contact for Two Pole MCCB, you cannot use it for SDE information.