Bring all of your project information together, and then export the data as a PDF or spreadsheet.Watch the video
Search through articles relevant to your industry.Read now
Schneider Electric Australia Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Yes, two smaller Line Chokes can be connected in series for Altivar 31/61/71 Drives.
The drop voltage of Line Choke is approximately 3% of the supply voltage at nominal current. For two series connected Line Chokes he drop voltage will be approximately 6%. So care must be taken to compensate this voltage drop, by supplying the Drive with a minimum of nominal Line Voltage plus 6% (Example for 400V supply, it should be 424V).