Bring all of your project information together, and then export the data as a PDF or spreadsheet.Watch the video
Search through articles relevant to your industry.Read now
Schneider Electric Australia Website×
TSXSCPCM4030 cable is required from TSXSCP114 PCMCIA card to the Modbus branching device TSXSCA50 for connecting other RS485 device on the Modbus Network.
In case TSXSCA50 Modbus branching device is not used, you can connect this cable directly to Modbus RS 485 device. For this you have to connect Green/White (Green wire with White Strips) and White/Green (White wire with Green strips) wires to the Tx (Transmit) and Rx (Receive) pins respectively of the RS 485 Port of the Modbus device.
Refer attachment for the pin out details of this cable for different connections.
Get the latest on new products, best practices and innovation from Schneider Electric.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!